TYPE HA-HESI High Energy Spark Igniter System
The Faber TYPE HA-HESI 12 Joule High Energy Spark Igniter System is a non-fouling, high energy device (NFPA class 3 special igniter) designed to directly ignite all liquid and gaseous fuels including bunker C. With its built in design characteristics, both fouling and blowing out are impossible. Applications include ovens, flares, incinerators, kilns, gas burners, oil burners and turbines (marine and gas).
TYPE HA-HESI High Energy Spark Igniter System Components
Probe Assembly with Optional Retract and Limit Switch Assembly
PowerArc Power Pack Assembly – NEMA 4, 4X and 12 Enclosure Options Available
The Faber TYPE HA-HESI High Energy Spark Igniter has proven to be a superior substitute for:
- #2 Oil Igniters through lowered maintenance
- Gas Igniters through lower installation costs
- Hand Torches by a safer and more reliable source of ignition
The Faber TYPE HA-HESI High Energy Spark Igniter operates as follows:
1. A transformer steps up the voltage to 2500 Volts AC
2. The circuit is rectified to DC
3. A capacitor is charged and then discharged through a sealed gap and a special semi-conductor tip
The most efficient location for the Faber TYPE HA-HESI High Energy Spark Igniter probe tip is in the outer edge of the spray. It may reach this spray either through a hole in the diffuser or around the diffuser cone. When ignition takes place the tip must be retracted from the high temperature zone.
Electrical Input – 100 – 130 VAC or 200 – 240 VAC, 50 – 60 HZ, 500 VA (jumper select input voltage)
Electrical Output – 2000 Volts DC, 12 Joule pulses at 9 – 12 HZ
Duty Cycle – 5 minutes on with 30 minute cool down
Spark Gap – Viewable and Replaceable
- Cylinder Bore – 2″
Cylinder Stroke – 6″ to 24″ in 2″ increments
Solenoid – 4 way – 11 watts
Position Switch – 10 Amps, 120 VAC, 1 N.O. and 1 N.C. contact
Depth Adjustment – +3″ or -3″
Operating Pressure – 15 PSIG minimum
- Electrical Disconnect – MS type
Mechanical Disconnect – Pipe union
Probe Tip – 446 Stainless Steel – 12″ standard
303 Stainless Steel – 3 7/8″ optional
FABER HA-HESI HIGH ENERGY IGNITER PROBE INSTALLATION INSTRUCTIONS
To download our high energy igniter probe installation instructions in PDF form please click on the image to your left.
NEED REPLACEMENT PARTS?
- Follow the link below: